Harmonic Modeling and Experimental Validation of the Converters of DFIG-Based Wind Generation System
Complexity 2019:1-13 (2019)
AbstractThe double-fed induction wind generator- based wind generation system contains power electronic converters and filter capacitor and inductor, which will bring about high-frequency harmonics under the influence of controllers. Aiming at this problem, this paper studies the relation between the output current and the harmonic source at grid-side and rotor-side converters based on their control features in the DFIG system. Furthermore, the harmonic equivalent models of these two converters are built, and the influence of different factors on harmonic features is explored from four perspectives, i.e., modulation method, altering controller parameters, altering output power, and the unbalance of three-phase voltage. Finally, the effectiveness of the proposed model is verified through the 2 MW DFIG real-time hardware-in-the-loop test platform by StarSim software and real test data, respectively.
Added to PP
Historical graph of downloads
Similar books and articles
Finite Control Set Model Predictive Control for Complex Energy System with Large-Scale Wind Power.Yang-Wu Shen, Jin-Rong Yuan, Fei-Fan Shen, Jia-Zhu Xu, Chen-Kun Li & Ding Wang - 2019 - Complexity 2019:1-13.
Coordinate Control of Power/Current for Grid-Connected Inverter Based on PCI Controller Under Unbalanced Grid Conditions.Chencong Zhao, Jun Liu, Zhouhua Xie & Feihang Zhou - 2019 - Complexity 2019:1-14.
Boost Converters’ Proximate Constrained Time-Optimal Sliding Mode Control Based on Hybrid Switching Model.Asghar Taheri, Amir Ghasemian & Hai-Peng Ren - 2019 - Complexity 2019:1-14.
Energy Yield, Power Quality and Grid Integration of Wind Energy Converters.R. E. Hanitsch - 2005 - In Alan F. Blackwell & David MacKay (eds.), Power. Cambridge University Press. pp. 1200.
Design and Application of Wind Power Peak Control Technology.Songyi Zhu - 2014 - Journal of Power and Energy Engineering 2:23-28.
Complexifier Method for Generation of Coherent States of Nonlinear Harmonic Oscillator.R. Roknizadeh & H. Heydari - 2015 - Foundations of Physics 45 (7):827-839.
An Effective Technique for Reducing Total Harmonics Distortion of Multilevel Inverter.G. Nageswara Rao, K. Chandra Sekhar & P. Sangameswararaju - 2018 - Journal of Intelligent Systems 27 (3):433-446.
The Effect of High-Frequency Parametric Excitation on a Stochastically Driven Pantograph-Catenary System.R. H. Huan, W. Q. Zhu, F. Ma & Z. H. Liu - unknown
A Plea for Automated Language-to-Logical-Form Converters.Joseph S. Fulda - 2006 - RASK 24:87-102.
Computer Modeling and Simulation: Increasing Reliability by Disentangling Verification and Validation.Vitaly Pronskikh - 2019 - Minds and Machines 29 (1):169-186.
Discontinuous Perturbations.Ramchander R. Sastry & John R. Klauder - 1997 - Foundations of Physics 27 (1):81-91.
Performance Analysis of Reheat Steam Temperature Control System of Thermal Power Unit Based on Constrained Predictive Control.Xiaoli Li, Jian Liu, Kang Wang, Fuqiang Wang & Yang Li - 2019 - Complexity 2019:1-12.
Multivariable Adaptive Variable Structure Disturbance Rejection Control for DFIG System.Akbar Tohidi, Oveis Abedinia, Masoud Bekravi & Nasser Ojaroudi - 2016 - Complexity 21 (4):50-62.
Hörmander Systems and Harmonic Morphisms.Elisabetta Barletta - 2003 - Annali della Scuola Normale Superiore di Pisa- Classe di Scienze 2 (2):379-394.
Adaptive Algorithm for Solving the Load Flow Problem in Distribution System.Vipin Kumar, Shubham Swapnil & V. R. Singh - 2018 - Journal of Intelligent Systems 27 (3):377-391.